This is our favourite pool/spa heater on the market today. The AstralPool ICI Gas Heater is the first of our Next Generation gas heater range. With the option of Natural or LPG gas, the ICI is available in 200MJ/h and 400MJ/h sizes with indoor and outdoor models to suit every pool owners needs. The ICI is also the only full-modulating mid-efficiency heater on the market, meaning that it can modulate its heating capacity to ensure a smooth steady control of heat to the water. This can assist with increasing life of product and reduce maintenance costs. Comes factory-fitted with standard AstralPool connections for easy plumbing installation, plus easy connectivity in the AstralPool Viron connect automation system, putting control in the palm of your hand. Call or email us today for an all-inclusive quote which includes installation and a gas compliance certificate issued by one of our licensed gas plumbers.
AstralPool ICI Gas Pool Heater
F1 - fault on AstralPool/Hurlcon gas pool heater
This is when the thermostat reads over 45degrees. Could be due to overheating or corrosion damage to the sensor.
F2 – fault on AstralPool/Hurlcon gas pool heater
This is a fault with the HiLimit sensors either reading that the water temperature is too high coming in or out of the heater. We have found through our 10 years of experience that this is the most common fault of all the heaters. However we find that more often than not there is a leak from the heater which has caused the sensors to slightly corrode.
F3 – fault on AstralPool/Hurlcon
This is just a simple thermistor fault and more than likely needs replacement.
F4 – This is a fault on the older Hurlcon MX series and JX heater
Signifies a flame roll out. Best to get this checked ASAP as more than likely your heater is seriously damaged.
F6 – This fault occurs on the AstralPool/Hurlcon heaters
When the air pressure switch or the overheat HiLimit175 has tripped. Possible causes are a blockage to the flue which is causing the air to compress within the heater or a damaged sensor on the flue.
F7 – This fault is occurs with the Viron and ICI range of AstralPool heaters
When there is a blockage to the condensate drain. However we have found that after some time with the heaters condensing that the float switch at the bottom of the heater calcifies and needs replacement.